Economical, reliable, easy to use pool sanitiser for safe and sparkling pool water. The Davey Ecosalt delivers swimming pool water sanitisation economically and for small to medium size pools.
Featuring 13 gram / hour to 26 gram / hour output, reverse polarity cell for longer life and easy maintenace as well as models with a digital time clock, the Davey EcoSalt gives you set and forget convenience and crystal clear swimming pool water
Davey - Salt Water Chlorinators - EcoSalt
DAY TO DAY OPERATION
Four Prime rules must be observed if your unit is to give the best possible service:
The importance of pool stabiliser cannot be over – emphasised. It is essential in helping retain chlorine in your pool. Chlorine is rapidly dissipated by sunlight and the use of stabiliser will reduce this dissipation substantially. Without stabiliser, it may be necessary to run the Unit for up to three times as long!
Stabiliser should be added at the rate of 500 grams for every 10,000 litres of water. Stabiliser should be maintained at a level of 30 – 50 ppm. Before adding more stabiliser, have your pool water analysed at your pool shop to ensure that you do not add too much.
2. pH AND TOTAL ALKALINITY:
A correct pH level must be maintained to prevent problems such as black spot, staining, cloudy water, etc. An incorrect pH level can damage the pool. Correct pH levels are as follows; Fibreglass – 7.2 to 7.4 Concrete & tiled – 7.4 to 7.6 If you allow the pH level to rise to 8.0 or above, the chlorine required could be as much as three times the normal amount.
Total Alkalinity should not be confused with pH, although the two are closely related. Total Alkalinity determines the speed and ease of pH change. It is measured in ppm – the ideal range is 80 – 150 ppm, or refer to your pool professional.
You should use a test kit which includes a test for Total Alkalinity. Low Total Alkalinity can cause unstable pH levels – i.e. An inability to keep the pH constant may cause staining, etching and corrosion of metals. High Total Alkalinity will cause constantly high pH levels.
3. SALT LEVELS:
Salt is the essential element by which your Unit operates. Not enough salt means not enough chlorine - this simple rule governs the total operation of your ChloroMatic®, and insufficient salt will damage your Cell.
RECOMMENDED SALT LEVEL RANGE: 4000 - 6000ppm
Warning: Some people recommend that you put salt directly in the skimmer box. This is a very poor practice as it allows very high concentrations of salt to be passed through your filtration and other pool equipment.
Salt is NOT used up in the process of producing chlorine or by evaporation. Salt is only lost through back - washing, splash - out, overflow or by leakage from the pool or plumbing. Winter rains can dilute the salt solution in your pool; therefore salt levels should be checked during this season. In colder water, the ChloroMatic should be set to Winter Mode. (Refer Winter Mode page 8).
Low salt levels will destroy the coating on the Anode plates and will void all Warranty.
The EcoSalt has a built in warning indicator to minimise damage resulting from insufficient salt levels, however, the ultimate responsibility is on the owner to ensure adequate salt levels are maintained all year round.
4. RUNNING TIMES:
These instructions cover EcoSalt for residential use only.
If you run your chlorinator for 24 hours a day, or for long periods, the Cell life will be greatly reduced. It is important that the correct model EcoSaltTM has been installed on your pool. Many models are available from Davey to cope with small courtyard pools up to commercial applications. (Consult your local EcoSaltTM Dealer for more information).
Note: The EcoSalt guarantee does not apply to commercial or semi-commercial installations, i.e. where the system runs more than an average of 8 hours per day over the year. Guarantee on commercial and semi-commercial installations is 12 months only on both power supply and cells.
The EcoSaltTM must be run daily to generate sufficient chlorine to sanitise the pool. During Summer this is approximately eight hours per day, preferably in two periods - between 6.00 and 8.00am and between 5.00 and 11.00pm. Night time is preferable because chlorine dissipates rapidly in direct sunlight. If these running times are observed, and the Cell is functioning correctly, your pool will have sufficient chlorine when tested in the morning.
If the level is too low either longer running times are required or the Sanitiser Output Control needs to be adjusted to maximum. Harsh local conditions such as traffic pollution or wind borne dust require different running times, in which case, seek advice from your pool shop. During Winter approximately 4 to 6 hours a day should provide enough chlorine. Without sufficient filtration/chlorination, your pool will never function correctly. ALWAYS RUN THE FILTER WHEN SWIMMING IN THE POOL. In extremely hot weather or during periods of heavy bathing loads, the running time may need to be extended to 10 - 14 hours per day.
In some cases you may find your chlorine level to be too high. To determine if this is the case, run your filter/ chlorinator for the suggested times/chlorine production level and test your pool water on the morning after operation. If your chlorine test shows a high level of chlorine, either the running times can be reduced slightly, or the Sanitiser Output Control can be turned anti - clockwise. Test your chlorine level again the following morning at around the same time. If your chlorine level is still high, repeat the above process until the correct level is attained.
Periodically, especially during extremely hot conditions, it may be necessary to boost the amount of chlorine in your pool in order to maintain absolute sanitation of the water. This can be achieved by adding either liquid or granulated chlorine. If granulated chlorine is added, the Cell must be checked regularly, since the additives from this product will clog the electrodes. Alternatively, extend the running time of your EcoSalt.
WARNING: Follow safety instructions provided with the Hydrochloric Acid or cleaning solution. When handling Hydrochloric Acid, the use of eye protection, mask and gloves are highly recommended. Extreme caution should be taken whenever handling Hydrochloric Acid or Cell Cleaning Solution.
No Chlorine Production - Check for
1. Main power outlet switched off
2. Chlorinator not plugged into main outlet
3. Pump not plugged into Chlorinator
4. Time Clock set to Off position/Power switch turned Off
5. Sanitiser Output Control turned to “o” setting
6. Chlorinator fuse blown
7. Dirty Cell
8. Filter needs back washing
9. Gas Sensor not connected
10. Insufficient water flow through cell
11. Running times incorrect
12. Main house fuse blown
13. Pump motor faulty
Low Chlorine Production - Check for
1. Dirty Cell - clean if required
2. Filter needs back washing
3. Cell failing
4. Pool stabiliser too low
5. pH too high
6. Salt level too low
7. Running time inadequate
8. Sanitiser output control set too low.